Voltage Regulator AVR MX341 MX341-2 for Stamford Generator
STAMFORD MX341 AVR Product Specification Download.pdf
High quality replacement model for MX341 MX341-2 AVR for Stamford Generator with reasonable price!
Replacement Models:AS440, AS480, SX440, SX460, MX341, MX321, MX450
Original Modules: AS440, AS480, SX460, MX341, MX321, MX450, MX342, MX330, EBC-1, RSK1001, RSK2001, RSK5001, RSK6001
The Brands mentioned here are for reference purpose only, our parts can exactly replace the original ones.
Stamford MX341 VOLTAGE REGULATOR is a two phase sensed Automatic Voltage Regulator and forms part of the excitation system for a brush-less generator. Excitation power is derived from a three-phase permanent magnet generator (PMG), to isolate the VOLTAGE REGULATOR control circuits from the effects of nonlinear loads and to reduce radio frequency interference on the generator terminals. Sustained generator short circuit current is another feature of the PMG system.
The Stamford AVR MX341 senses the voltage in the main generator winding and controls the power fed to the exciter stator and hence the main rotor to maintain the generator output voltage within the specified limits, compensating for load, speed, temperature and power factor of the generator.
Soft start circuitry is included to provide a smooth controlled build up of generator output voltage.
A frequency measuring circuit continually monitors the shaft speed of the generator and provides under-speed protection of the excitation system by reducing the generator output voltage proportionally with speed below a pre-settable threshold. A further enhancement of this feature is an adjustable volts per Hertz slope to improve engine recotime on turbo charged engines. Soft start circuitry is included to provide a smooth controlled build up of generator output voltage.
Uncontrolled excitation is limited to a safe period by internal shutdown of the VOLTAGE REGULATOR output device. This condition remains latched until the generator has stopped.
Provision is made for the connection of a remote voltage trimmer, allowing the user fine control of the generator's output.
An analogue input is provided allowing connection to a Newage Power Factor controller or other external devices with compatible output.
The VOLTAGE REGULATOR MX341 for Stamford has the facility for droop CT connection, to allow parallel running with other similarly equipped generators.
Voltage 190-264V ac max, 1 phase, 2 wire
Frequency 50-60 Hz nominal
POWER INPUT (PMG)
Voltage 140-220V ac max, 3 phase, 3 wire
Frequency 100-120 Hz nominal
Voltage max 120V dc
Current continuous 2.7 A
Intermittent 6A for 10 secs.
Resistance 15 ohms minimum
+/- 1% (see note 1)
0.03% per oC change in VOLTAGE REGULATOR ambient (note 2)
SOFT START RAMP TIME
TYPICAL SYSTEM RESPONSE
VOLTAGE REGULATOR Response 10 ms
Filed current to 90% 80 ms
Machine Volts to 97% 300 ms
EXTERNAL VOLTAGE ADJUSTMENT
+/-10% with 1 k ohm 1 watt trimmer (see note 3)
UNDER FREQUENCY PROTECTION
Set point 95% Hz (see note 4)
Slope 170% down to 30 Hz
UNIT POWER DISSIPATION
12 watts maximum
Maximum input +/- 5V dc (see note 5)
Sensitivity 1v for 5% Generator Volts (adjustable)
Input resistance 1k ohm
QUADRATURE DROOP INPUT
10 ohms burden
Max. sensitivity: 0.07 A for 5% droop 0PF
Max. input: 0.33 A
OVER EXCITATION PROTECTION
Set point 75 V dc
Time delay 10 seconds (fixed)